The rheostat is connected in the system undergoing test by placing the switch (53 ) in the aquot;RHEOaquot; position (par. 62). \alt;agt;le. ... of the main control panel, is a 3- position (on-off-on) , single- pole, double-throw, 20-ampere. 30-volt dc, toggle switch. ... (Refer to paragraph 63 for further instructions for connecting these rheostats.)anbsp;...
|Title||:||Operator and Organizational Maintenance Manual (including Repair Parts and Special Tool Lists)|